Welcome to Firesense Website
The FireSense Remote Release/StopGas station is for use with all FireSense Gas Control/Suppression systems.
The unit contains a break glass unit for the release, and a push on/push off switch for isolation of the automatic activation of the suppression gas. This will not isolate the manual activation function.The unit is connected to the gas control panel via four (4) cables. On activation of the Stop Gas Switch, a zero voltage signal is sent via the Stop line to the panel. Confirmation of the Stop is signalled back to the Stop Gas Station, activating the stop gas switch lamp and buzzer. StopGas activation prevents automatic operation of the system. Manual release will over-ride StopGas.